- Activities Carried Out in till Date
- Activities Planned for December 2016
Due to the huge amount of concrete work involved in Raft foundation and the availability of very little work space, it was decided that the raft foundation would be done in several sections. First section was cast on 14th November and the 2nd was cast on 28th November. To ensure compliance with Specifications, a constant check was maintained on Site for maintaining the quality of concrete mix at desired level. For each section, 12 nos. cubes (6” x 6” x 6”) of concrete samples were prepared to be tested at 7 and 28 days. The mix design for 5500 psi concrete has already been finalized and independently tested from CWO Laboratory. Additionally, “Slump” is also regularly measured during concrete works and an average of approx. 5 inch value has been maintained as per Specifications. Trial mixes for 7000 psi concrete have been prepared and would be tested at 7 days and 28 days before column concrete is poured.
Record of Slump and compressive strength test is constantly maintained on Site along with that of material consumption and necessary Approvals etc. In addition to that, actual measurements are also incorporated in drawings and a complete set of up to date “As-Built” drawings would be printed out once the raft foundation is 100% complete. “Shop Drawings” (as per finalized list) are also being prepared as and when required and record of them being maintained separately.
To ensure proper bonding at the construction joints, SBR Latex was used. Additional # 4 steel bars were provided at mid depth for improved bonding between adjacent sections of Raft concrete.
Due to the generally upward trend in prices of various items, the Contractor has placed advance orders on various items to “lock” their prices. Some such items are related to electrification and plumbing works. Samples of materials procured, along with all relevant documentation, are maintained on Site office. As part of Due diligence, I visited the manufacturing facility of M/s Fast Cables ltd in Lahore before approval was duly given for the same. As a rule, Director AIS is constantly onboard in the Approval process and his approval is duly documented prior to all procurements.
The initial drawings had shown Raft concrete without any construction joints. Construction joints were proposed and duly incorporated after consultation with Structural Engineer at Archcorp.
The final section of Raft foundation is the largest and it has been proposed by Contractor that it be carried out in two equal halves. This has been shared with Archcorp and would be done only if the Structural Engineer gives formal approval.
Lay out of Steel in final section of Raft foundation
Concrete work in final section of Raft foundation ( 5,500 psi)